Local Code Amendments
- Switches controlling stairway lighting must be lighted in the off position (residential only).
- Switches controlling stairway lighting must be within 6’ of the top and bottom of each stairway (this includes basement stairs)
- (residential only).
- Per the Bedford Fire code gas furnaces are required to have fire-matics and emergency shut off switches located outside the point of entry to the area where the device is located.
- A wall switch must control lights in attics and other storage areas.
- The maximum water temperature at domestic lavatories and kitchen sinks is 130 degrees F and 120 degrees F at showers and tubs.
- The maximum water temperature at commercial lavatories and personal hand wash stations is 130 degrees F.
- The maximum water temperature shall be obtained using a mixing valve located either at the hot water source or at each fixture required to have the maximum temperature limited.
These amendments are part of the Bedford municipal code and related to the Building Construction Ordinance (PDF). Amend the IBC section outlining Architect/Engineer responsibilities during construction by adding this information.
When the laws of the State of New Hampshire require that construction documents be prepared by registered architects or engineers or the plans do not meet the prescriptive requirements of the code, the registered architects or engineers who have prepared plans, computations and specifications or the registered architects or registered engineers who have been retained to perform construction phase services, shall perform the following tasks for the portion of the work for which they are directly responsible:
- Review, for conformance to the design concept, shop drawings, samples and other submittals, which are submitted by the contractor in accordance with the requirements of the construction documents.
- Review and approval of the quality control procedures for all code-required controlled materials, structural tests and special inspections.
- Be present at intervals appropriate to the stage of construction to become generally familiar with the progress and quality of the work and to determine, in general, if the work is being performed in a manner consistent with the construction documents and accepted engineering practice standards.
- The design professional shall submit to the building department documentation verifying compliance with the above requirements at regular intervals, which shall be noted at the time of permit issuance.
- The tasks listed in this section are in addition to requirements for structural observation or other duties specified in Section 1704, Section 1709 or elsewhere in the adopted International Building Code.
Add a new section regarding Architect/Engineer qualifications:
- When the requirements of codes dictate there shall be design professionals preparing plans; those professionals shall have their license based upon the discipline required for the plans being prepared. Any design professional wishing to stamp plans for a discipline other than the one his or her license is based upon may be required to submit additional documentation validating his or her competency in the additional area of design.